||A thick-film reinforced epoxy internal lining formulated for corrosion control of chemical tanks and aggressive chemical immersion. Spray applied at 20 to 50 mils. Series 390 exhibits superior resistance to a wide range of chemicals with excellent physical properties for long term durability and service life. Refer to the Tank Armor® Chemical Resistance Chart. The Series 390 touch-up kit may be used to repair other Tank Armor linings. Contact Tnemec for more information.
||1232 Blue. Note: Epoxies chalk and yellow with age, extended exposure to UV and artificial lighting.
||Series 351 Tank Armor®
||20.0 to 50.0 mils (508 to 1,270 microns) one coat with multiple passes.
These times are based on a 20.0 mil (500 micron) dry film thickness. Higher film thicknesses, insufficient ventilation or cooler temperatures will require longer cure times. This coating commonly develops an amine-blush during cure. While this condition will not adversely affect performance of the coating, this blush must be removed by aggressive sweep blasting before applying additional coats. During high humidity conditions, it is recommended that the application be done while the temperatures are increasing. Cure time to achieve a minimum Shore D Hardness of 81 or Barcol GYZJ 935 hardness of 66 for immersion service is 24 to 36 hours. In order to obtain an accurate reading, the minimum DFT must be 30 mils.
|Temperature || To Touch || To Handle || Immersion|
| 75°F (24°C) || 2 hours || 3 hours || 24 to 36 hours |
|Volatile Organic Compounds
||0.30 lbs/gallon (35 grams/litre)
||0.27 lbs/gal solids
||1,604 mil sq ft/gal (39.4 m²/L at 25 microns). See APPLICATION for coverage rates.
|Number of Components
||Two: Two Part A (epoxy) to One: Part B (amine)